Monday, June 14th, 2021
Dewar Gas Services were called by the client to inspect a leaking heat pump. Upon inspection, we found that it was poorly installed by the previous plumbing company less than 5 years ago and as they no longer traded, we advised the client to replace and upgrade the system to a Viessmann Vitocal 200-A 13kW (COP of 4.72A7/W35) heat pump combined with Vitocell 300-B 300l A-rated cylinder (standby heat loss of 1.06kW/24hr).
In order to achieve the minimum volume requirement to allow the heat pump to perform its defrost cycle and to prevent it from cycling, a Vitocell 100-E 46l wall hung buffer was used. A low loss header was used with a secondary pump, two motorised valves, and two-room stats to allow for separate control to the ground floor and first-floor heating zones.
We provided the installer with a full system design schematic for both the underfloor heating and heat pump. By doing this it made the installation and commissioning of this project simple and trouble-free. Precision Heating commissioned the installation, and both the client and installer were delighted with the end product.
We provide 24/7 emergency Dublin Gas & Oil Boiler Services, Repairs and Replacements to 1000’s of customers for their homes and business all around Dublin.